I am on a no ac service call where the indoor unit runs yet outdoor unit doesn’t start. I find power going through the contactor to the motors yet nothing is running. I then feel the compressor and it is hot. I test the motor windings and they are open OL. I run water on the compressor to cool it off. The windings close I find a defective capacitor, replace the capacitor. Turn the system back on compressor and condenser fan motor start right up. This ac system will live to keep my client comfortable.
Ссылка на страницу с видео:
Ссылка HTML на страницу с видео:Код для вставки плеера: